Jump Start Manufacturing Company introduced the install […]
Jump Start Manufacturing Company introduced the installation height and spacing of fire emergency lights:
1. Installation height of double-head fire-fighting lighting emergency light
Emergency lighting for fire evacuation should be installed on the wall or ceiling (applicable to fire double-head emergency lighting, fire emergency ceiling lights, fire emergency downlights/spotlights, etc.). Double-head fire emergency lighting is often installed above the door frame of fire evacuation passages or safe escape exits or on the wall, at the corner of stairs, etc., and installed at a position about 2.2 meters from the ground. Longer evacuation passages should be installed in accordance with the fire protection system. According to the guidance of the department, or according to the brightness of the emergency lamps in the actual use place, the density of the lamps should be appropriately increased, and the installation should be reasonable. Double-head fire emergency lighting can also be installed on the column (such as electronic city, shopping mall, station, etc.).
2. Installation position of fire emergency ceiling lamp
Ceiling lights for fire emergency lighting are generally installed on ceilings or ceilings. There are screw holes for installation on the chassis of emergency luminaires. First, drill holes on the ceiling and insert rubber plugs according to the mounting holes reserved for the lamp panel. Fix the chassis of the luminaire with the screws first, then install an electronic energy-saving lamp or incandescent bulb in the lamp panel as required, turn on the power, tighten the lampshade, and finally test the emergency function of the luminaire.
3. Installation position of fire emergency downlight/ceiling light/spotlight
Ceiling/recessed fire emergency downlights. Ceiling lights/spotlights are generally installed on the ceiling. A circlip device is provided on the edge of the luminaire for fixing the luminaire. When installed, it is opened at the top of the selected ceiling. After connecting the input power cord, squeeze the circlip with your hand, push the circlip upward, and insert the bottom of the emergency lamp into the hole, check whether the installation of the lamp is level, and then press the test button to check the emergency function of the lamp Is it normal.