Jump Start Manufacturing Company introduces maintenance […]
Jump Start Manufacturing Company introduces maintenance knowledge of emergency power supply:
1. Troubleshooting. When an EPS has an internal failure, it is necessary to judge the status of the EPS according to the EPS self-check results and the maintenance personnel according to the test situation. When the output of the circuit breaker and the battery are damaged, the EPS will directly notify the fault location.
2. Laying the line. The emergency lighting line is arranged separately, and each evacuation exit has an independent emergency lighting line control loop, which cannot interoperate with the general lighting line. The insulation resistance of the wire can only be tested after the wire is connected. The emergency lighting circuit cannot be mixed with the general lighting circuit.
3. Lighting device. You can use ordinary energy-saving lamps and fluorescent lamps, you can also use prefabricated lighting and residential lighting, and the refuge indicator light needs to use fire-certified products. The sign lamps are made of non-flammable materials, and their arrows must be consistent with the direction of avoiding fire. All metal parts installed must have corrosion resistance.
4. Installation of the distribution network. The installation technology of the emergency lighting distribution box is the same as that of the general lighting distribution box, and the emergency lighting distribution box needs to be different from other general lighting distribution boxes. The structure and electrical components of the emergency lighting distribution box need to have heat and fire resistance.